SP-N1 Single One Door TCP/IP Network Access Controller For
building, apartment etc
Product model: SP-N1
S-N1 (Panel only)
Product name: Single Door Network Access Controller
Working temperature: - 40 ~ 60C
Product size: L273*W228*H65mm
Support Datebase: Access and SQL
User capacity:20000 users
Records(offline): 100,000(can be saved on controller permanently)
Power Supply:12VDC ,4-7A
Input Format of Reader:Wiegand 26 (All card reader with compatible
protocol, such as HID, EM , Mifare etc)
Quantity of Readers:2(In&Out for one door)
Way of opening door: card; card + PIN; multi-cards; first card etc
Door opening time extending setting:1-600 seconds(adjustable)
Opening door by multi-card: Swipe multiple cards, door will be
With software, control one door
Can set who/when/how can access
Conventional Function:Access;Time&Attendance;Offline operation;
real time supervision; photo display; mass storage; flexible user
privilege setup;remote unlocking; multi-user supervision
Professional function:Anti-passback and
Anti-tail;Interfacelocking;Intimidation alarm;Integrated fire
control;Interlocking;Multi-card unlocking etc
Language of Software kit: Chinese & English
Network Access Control (SP-N1/2/4)
1, Q: How many doors can the device control?
A: One device can control 1/2/4 doors. Multiple devices can control
infinite doors theoretically(Need to install in same LAN)
2, Q: Which Wiegand format is it ?
A: It supports Wiegand 26 bit. Wiegand 34 bit can be customized.
3, Q: How to login in software?
A: User:abc. Password:123
4, Q: What is the password for extended function?
5, Q: Can i use other language besides English?
A: Sorry,SP-N series only support Chinese & English. SP-G
series support other languages.But you need to translate by
6, Q: Can you offer SDK?
A: Sorry.SP-N series don't have SDK. SP-G series have.
7, Q: I need record in two-way,in and out. Is it possible ?
A: SP-N1,SP-N2 both support two-way record.SP-N4 supports one-way
8, Q: What kind of cables should i use when installing?
A: ①The line of electric lock to controller, it’s recommended to use
two-wire power line, the cross-sectional area of 1.0 mm2 or more.
If over 50 meters, it’s considered to use more thick line or
multiple parallel, the longest no more than 100 meters. The line of
door sensor to controller, it’s recommended to use two-wire power
line, the cross-sectional area of 0.22 mm2 or more If no need to
know door open/close status online, or door long-time not close
alarming, either illegal intrusion alarming, interlock function,
etc., the door sensor can be without wiring.②The line of card
reader to controller, the cross-sectional area≥0.22mm2,CAT.5 or UTC
are both applicable. If no need to identify the valid or invalid
card by the feedback of sound and light, it can be without
connecting BEEPER (blue) either LED (brown). It’s better
twisted-pair for lines Data0 and Data1. The distance of card reader
to controller can’t be over 100meters,proposed within 80 meters. If
the distance exceeds 50meters, it’s proposed to bold or share as
aggregate to provide power supply to card reader, which is helpful
to improve the functions of card reader.③The line of button to
controller, it’s recommend to use two-wire, the cross-sectional
area 0.221mm2 or more. ④TCP/IP communication line: It’s the same
with computer network wiring, controller connecting to switch or
HUB with ordinary network cable, distance less than 100meters. The
longer distance, the higher quality requirement of cable.⑤220V AC power cable: three-wire power supply, the cross-sectional
area 1.0mm2 or more. It’s required that power supply must be
grounded to prevent from power interference.